Question about Heating & Cooling
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
SOURCE: re: combi boiler.
if you have hot water at the taps but the heating isn't working make sure the thermostat is set high enough for the boiler to run check the time clock settings are on.
if these are working it could be a faulty diverter valve switch not sending a signal to the boiler to run.
Posted on Mar 30, 2009
If there is a hi-limit switch, maybe it's open, reset the switch, and monitor the temperature, if the temp. increases over the set temp. replace stat, and clean lime off from the tank, if does not have a filtering system
Posted on Apr 21, 2009
SOURCE: I have an Alpha CB28
try tapping the 3 relays on the pcb,"thats the circuit board under the front cover...
it sounds like a dodgy relay thats starts up the pressure fan in next to the flue....
maybe a dry solder joint,maybe a new relay needed....
its a common fault on this model..
Posted on Aug 02, 2009
SOURCE: Baxi solo 3 70pf boiler problem
This happened to me and it was a rubber pipe inside had perished so it was detecting a loss of pressure. You can see it if you take the main cover off and also the front clipped on cover. Its at the top on the right. You need to replace it with heatproof pipe. Good luck!
Posted on Jan 05, 2010
Tips for a great answer:
Apr 30, 2017 | Water Heaters
Jun 23, 2014 | Heating & Cooling
Jan 23, 2014 | Honeywell Programmable Thermostat Heater
Feb 03, 2013 | Hardware & Accessories
Nov 06, 2012 | Heating & Cooling
Mar 22, 2017 | Water Heaters
Oct 28, 2009 | Heating & Cooling
May 15, 2009 | Water Heaters
74 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: