Question about Intertherm Heating & Cooling
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
It could likely be the fan control switch. Open up the cabinet, and you'll see a metal box, roughly 7x9x2" inside, with the blower switch located on the top edge of it. There are usually two screws holding the lid on. Remove the two screws and the lid, and you'll see a couple of eye-shaped items side by side with 2-3 blue or orange wires running to them, each. They might have numbers on them such as 6263360 or 6263370. These are the limit switch and control switch, respectively. If your fan keeps cycling on and off, try replacing the control switch (6263370). The new part number for these switches are 626336 (limit) and 626337 (control). The control switch is also one of the cheapest (less than $10) places to start.
Posted on Oct 29, 2009
There is probably more than one limit switch. I'll have to get a wiring diagram of this unit. See if you can follow the wires from the wires from the limit switch and see if they go to another limit switch. Also you can put a jumper wire on the red wire and white wire on the unit outside and see if ti comes on.
Posted on Nov 03, 2009
On these of Furnaces the filters mount on the door. Remove the door you will notice grill on front. There should be a track on the back of the front door to slide filters down. Should take 2 filters.
Posted on Dec 06, 2009
Testimonial: "drifterray really helped. way to go apprentices!"
Tips for a great answer:
Apr 07, 2018 | Intertherm Heating & Cooling
Jan 02, 2018 | Intertherm Heating & Cooling
Dec 22, 2017 | Intertherm Heating & Cooling
May 10, 2017 | Intertherm Heating & Cooling
Apr 10, 2015 | Intertherm Heating & Cooling
May 15, 2014 | Intertherm P3RA-048K Air Conditioner
Feb 07, 2014 | Intertherm Heating & Cooling
Aug 28, 2017 | Intertherm Heating & Cooling
Aug 23, 2011 | Dayton Gas Furnace Heater
Nov 02, 2009 | Intertherm P3RA-048K Air Conditioner
102 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: