Question about Goodman CLQ36AR49 Air Conditioner
Jump connections at the stat. if it runs replace stat .. switch fan to on if fan blows you know 24 v is arriving and leaving stat to power blower. jump red to yellow to make compressor section run. jump red to green to make indoor fan run. in an emergency jump red to fan g and red to yellow and let run till cold then turn off breakers to outdoor unit till hot then on again. NOT recommended unless its deathly hot etc or system is hopelessly beyond professional repair
Posted on Oct 12, 2008
Control board low voltage problem
Posted on Aug 19, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Dec 21, 2015 | Heating & Cooling
Oct 31, 2013 | American Standard Trane Ge Gas Furnace...
Apr 05, 2013 | Heating & Cooling
Jul 15, 2011 | Heating & Cooling
Jul 13, 2010 | Danby Heating & Cooling
Oct 04, 2009 | Heating & Cooling
Jun 30, 2009 | Honeywell Electronic Programmable...
May 16, 2008 | Everest Refrigeration EMGR24 Commercial...
145 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: