Compressor went out on 4 ton unit. want to upgrade to 5 ton A/C. Have been told need bigger blower unit. Can I exchange to blower unit that will handle 5 ton A/C?

Posted by on

• Level 1:

An expert who has achieved level 1.

Hot-Shot:

An expert who has answered 20 questions.

Corporal:

An expert that hasĀ over 10 points.

Problem Solver:

An expert who has answered 5 questions.

• Contributor

Hi mans1930. You need to replace the whole inside blower unit, the coil as well as the blower. If not, there would be a very good chance of damaging your outdoor unit, namely by ruining your new compressor.

Greg.

Posted on Aug 18, 2008

Hi,
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
Good luck!

Posted on Jan 02, 2017

×

my-video-file.mp4

×

Related Questions:

What is the HP rating if a 3 ton air conditioner?

Hi, this depends on the compressor that is installed in this unit. It may be a Copeland scroll, a Tecumseh, its hard to say. Most compressors are around 2 hp for a 3 ton unit. On the data plate it will tell you the h.p. of the blower and condenser fan motors such as 1/4 h.p., or 1/3. If you can get the name and model numbers from the top of your compressor, you can call a a/c, Refrigeration parts house, wholesale and they will have it in there manuals. The B.T.U. rating for your compressor is 36,000. There are 12,000 BTU's per ton of cooling, this is something that almost no one knows, but now you do. If it were a smaller unit such as a 2 and 1/2 ton, it would be 30,000 B.T.U.'s. You can look at the model number of a unit and you will see numbers like this, 024, 2-ton, 030, 21/2 ton, and 036 a 3 ton unit and so on. Your compressor alone will be in the range of a 2 horse unit, which ever the brand of compressor they installed in it. Please don't forget to rate me on this as I know you will be kind. I will be here if you ever need help on repairs or trouble-shooting your unit in the future, just use my user name below.
Sincerely,
Shastalaker7
A/C, Heating, & Refrigeration Contractor

Sep 04, 2010 | Heating & Cooling

My weatherking outside compressor isn't big enough to handle my cooling needs. It is 1.5 ton unit, can I put a bigger ac unit onto this one without changing my heating system which is sufficient?

Note :your duct system may have been designed for a 1.5 ton and may need to be reconfigured for a size increase.
Your hvac contractor should know this?

Jun 14, 2010 | Weather King 10AJA4201AH Air Conditioner

I have a Lennox CH23.51 series coil unit using R22 freon installed one year ago. Compressor is 9 years old. Down the road when replacing compressor (R410A ), will CH23.51 unit be compatible after changing...

This evaporator core is R-22 / R-410A compatible. The Thermostatic Expansion Valve (TXV) is for R-22. If retrofitting to R-410A, a new TXV metering device would be required, but the evap. core itself could be re-used (as long as you stick with the same Tonnage you have now). If upgrading to a higher tonnage system (like going from 4-Ton to 5-Ton), then you would need a totally new evaporator core.

Jun 08, 2010 | Heating & Cooling

New copeland compressor wont start

Hello,By all means install a hard start kit on the cap.Your wiring is correct.A scroll compressor usally doesn't need a start kit but I have seen 5 ton units that take one.Check the compressor tag and make sure the compressor is not a 3 phase motor!

Apr 21, 2010 | Heating & Cooling

Compressor size

Square footage is how you determine what size of an AC you need, say two bedroom house with 1500 square feet would require a 3 ton unit but I would go to a 4 or 5 ton depending on brand and what you may do in the future, Like adding a bedroom or bathroom and how many people will be living in the house, a heat pump normally last longer the bigger it is and is more efficient than a smaller size. Just think like this, a 3 ton will run 30 minutes to an hour longer to cool the same space as a 5 ton so if the five ton does it 30 minutes faster it will not run as long. And when it has to pull down the temperature again it will do it much faster. So less run time means faster heat or cooling and less energy is used. I have found that the bigger units are made better and last longer as a general rule. And to understand the 3-ton and 5 ton let me say that it means how long it takes 3 tons of ice to bring the temperature down 10 degrees, the old BTU’s British thermal units. However the bigger the unit the more well built it is normally and the less maintenance required. 5 tons of ice would get it cooler faster. But one thing to keep in mind a heat pump is only good for 20 degrees temperature range, for instance if the high range is 80 then the low side would be 60 in order for it to be efficient so if you have it set in the house at 72 degrees on the high side and low side would be 52 degrees. But the larger the unit the less time it would take it to recover from the heat differential.

Jul 22, 2009 | Ruud UAKA042 Air Conditioner

What ton is my old Luxaire AC unit? it is model EESQ36

Sure but you need ot have an AC man to replace it and vac down the system plust change the dryer/reciever.

Jun 12, 2009 | Weather King 10AJA3601AH Air Conditioner

Air handler fan not working

Check the fan relay switch in the air handler.
Check the fan motor capacitor.
Check the fan blower wheel for binding.

May 25, 2009 | Heating & Cooling

How far from the house should the outside unit be located?

If your outdoor fan is a vertical discharge in other words if the fan blows the air up from the top of the unit then one foot from house is fine, but if it is horizontal discharge or blows it out the side then the airflow needs to be directed away from the house or the unit needs to be moved away from the house far enough that it doesn’t restrict the airflow.
For the blower running on high speed a 4 ton unit is usually 1600 cfm so on low cfm it may seem like high speed. There should be some speed taps on the indoor pc board and if you look in your installation guide it should tell you what taps you need to get the lower airflow if its not correct.
For the luke warm air in the 2 ton mode, the coil is a still 4 tons but the compressor now is only pumping 2 tons of refrigerant so the discharge temperature and head pressure will be much lower and that is what determines how much heat you get, so you will get less heat. The 2 ton mode is for times when you only need a little heat or cool, when you need more then you will get the 2nd stage which is the full 4 tons of heat.

Apr 21, 2009 | Heating & Cooling

Open Questions:

Related Topics:

82 people viewed this question

Level 3 Expert

Level 3 Expert