Question about Coleman Propane Forced Air Heater w/Electronic Ignition (50,000-80,000 BTU)
Unit keeps freezing over-we cleaned out front and back unit as instructed by a repairman but it still keeps freezing over
Make sure you let the blower run for a while after it freezes to make sure there is no more ice. Then run the unit. Check the refrigerant lines the large copper line that has insulation on it should be cold to the touch. If it runs for 10 minuits and is barely cold or warm you are low on refrigerant. If its starts out nice and clod then check your filter and retun ductwork for blockage you should not have noisy return air vents or that can indicate you have too small a return.
Also are the outdoor unit and indoor coil a match? Same tonage?
Is the furnace big enough to handle the tonage? (fan size)
Posted on Jul 27, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Mar 05, 2015 | World Heating & Cooling
on Dec 01, 2009 | Heating & Cooling
Dec 23, 2010 | Dimplex DS5598 Mid-Size Heater
Aug 28, 2010 | Goodman Heating & Cooling
Feb 23, 2010 | Coleman Propane Forced Air Heater...
Dec 30, 2009 | Desa International CBN30T Central Heating...
Jun 09, 2009 | Goodman GMS90703BXA Heater
Apr 25, 2009 | Coleman Propane Forced Air Heater...
Feb 15, 2009 | Lasko Ceramic Heater
May 15, 2014 | Coleman Propane Forced Air Heater...
42 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: