Question about Fujitsu Heating & Cooling
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Sounds like your compressor is seized or a start fault. If the unit is under five years old it should be under warranty. Call Fujitsu warranty out to have a look at it for you.
Contact details as follows
Sorry but either way I think your going to need a part there is very little that I can do unless your in WA.
Hope this helps
Posted on Jan 11, 2009
SOURCE: System will not start up.
This is a signal fault between the indoor and outdoor first make sure the dip switches are set start with the unit closest to the condensor set as unit 1 then next unit as 2 and so on the dip switches are inside the indoor unit on the pc board if you check the manual it will tell you which swithes to set, if this wasnt done when the units where installed they would have never worked i would also check the signal wiring between the wallmount and the splitter box / bc box and make sure there isnt a loose connection when you have ruled this out id say more than likely it is a faulty indoor board on the wallmounted unt
Posted on Apr 08, 2009
Tips for a great answer:
Jul 03, 2017 | Fujitsu Heating & Cooling
Mar 05, 2017 | Fujitsu Heating & Cooling
Jul 10, 2015 | Fujitsu ASU9RLS2 Single Zone Wall Ductless...
Jan 16, 2010 | Panasonic Heating & Cooling
Sep 12, 2009 | Intermatic & Indoor/Outdoor Rain Tight...
Jun 01, 2009 | Fujitsu Heating & Cooling
May 16, 2009 | Fujitsu 24R1 Air Conditioner
Jan 27, 2009 | Fujitsu 24C1 Air Conditioner
May 17, 2008 | Fujitsu 24C1 Air Conditioner
302 people viewed this question
Usually answered in minutes!