Question about Heating & Cooling
Hello, check to make sure you are getting 24 volts at the contactor coil, if you are and yet the contactor does not energize replace it. If you do not have 24 volts inspect the thermostat wiring and thermostat. If the contactor does energize but still the compressor or fan do not run then most likely you have a bad capacitor and must be replaced.
Posted on May 28, 2011
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Apr 27, 2011 | Oster 12-Bottle Wine Cellar - Black
Feb 01, 2011 | Samsung AS18A6RB Air Conditioner
Sep 17, 2010 | True Pizza Prep - TPP-67
Sep 09, 2010 | Carrier 38CKC036 Air Conditioner
Jun 21, 2010 | Carrier 38CKC036 Air Conditioner
Jun 18, 2010 | Ruud Central System Air Conditioner
Dec 24, 2009 | Heating & Cooling
Jul 12, 2009 | Goodman CLQ36AR49 Air Conditioner
Jun 25, 2009 | Carrier 38CKC018 Air Conditioner
Jun 01, 2009 | Heating & Cooling
50 people viewed this question
Usually answered in minutes!