Question about Teledyne Laars Laars Lite 2 Pool Heater 325,000 Btu / Propane Gas
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
You have no flame rectification.....LLD series heaters check for a signal through the flame to ground; if the module does not detect this signal, it go through two more trials for ignition and then lock out the module. There should be a flame rod and it may need cleaning. I use steel wool.
Posted on Jun 28, 2009
Hi should be horizontal crack pipe and see if gas is there do this with every thing off then pruge pilot line should have gas then
Posted on Feb 17, 2010
Do you replace the thermopile or check the milivolts?
Check the Pressure gas
You need replace all of them terminals and check again the milivolts at the gas valve
Posted on May 29, 2010
Tips for a great answer:
May 13, 2013 | Jandy Lx Pool & Spa Heater - Electronic...
Apr 17, 2012 | Jandy LXI 400 NATURAL GAS POOL HEATER -
Jun 15, 2011 | Hayward H Series Electronic Ignition...
Aug 10, 2010 | Hayward H400 High Wind Stack
Jul 17, 2010 | Hayward H Series Pool & Spa Heater 400k...
May 30, 2010 | Hayward 250kbtu Ng Pool Heater - Inground
May 27, 2009 | Pentair Minimax NT Heater
May 07, 2009 | Pentair MINIMAX NT TSI IGNITER
40 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: