Question about Intermatic EH40 - Electronic Water Heater Timer - NEMA 1 Indoor Steel Case
You posted under EH40 240Volt programmable timer.
If I understand correctly, you are testing the terminals when timer turns ON?
Test shows 120V between terminal 4 and ground wire.
Test shows 0 volts between terminal 6 and ground wire.
Test terminal 3 to ground -and- test terminal 5 to ground and make sure each tests 120V.
Test terminal 3 to terminal 5 for 240V.
If terminals 3 and 5 test correctly, but terminal 6 never has power, then relay inside timer has gone bad.
Contact Intermatic about 1 year limited warranty
Upvote the help.
And take advantage of fixya expert assistance live.
For a price, expert works with you while you work on timer or any do-it-yourself project.
Fixya is always less expensive than a service call.
Posted on May 29, 2011
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Sep 06, 2016 | Chevrolet S 10 Cars & Trucks
Dec 14, 2014 | 2005 Yamaha V Star 1100 Silverado
Mar 15, 2013 | Precor Efx 546 Version 1 Lower Body...
Oct 14, 2011 | Precor EFX 546i Elliptical Version 4
Sep 11, 2011 | General Electric Monogram® ZGU385NSMSS...
Jun 13, 2011 | 1997 Ford Explorer AWD
Apr 29, 2010 | 1997 Ford F150 Regular Cab
Aug 19, 2009 | LG DLE2532W Electric Dryer
Nov 29, 2008 | NetGear WPN111 RangeMax Wireless USB 2.0...
240 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: