Question about Sharp Heating & Cooling
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Possible low voltage condition would cause that kind of a problem. To small a cord without the ability to carry and maintain the voltage would cause a voltage drop. I would test the voltage supply and make sure it is within 10% of that required for your A/C to operate properly.
Posted on Jun 16, 2008
The fan motor is getting hot and going off on the internal overload in the motor.
This is caused by either a low voltage, a bad capacitor, or tight or dry bearings in the motor.
To check the bearings turn the power off to the unit, then spin the fan blade if it spins freely then the bearings are ok.
To check the capacitor you will need some kind of tester or you can buy a capacitor and replace it, that's what a lot of people do. They usually don't cost very much.
To check the voltage you will need a voltmeter and measure the volts at the unit.
Posted on Jun 09, 2009
Take it back to the dealer and have them fix it, could be a compressor froze up or a fan froze up. If you disconnect the compressor and turn it on and it trips the breaker the fan is probably
bad. If you disconnect the Fan and turn it on and it trips the breaker
it is you compressor.
Posted on Jul 16, 2010
Tips for a great answer:
Aug 27, 2014 | Heating & Cooling
Jun 07, 2011 | LG Electronic Window Air Conditioner
Mar 30, 2011 | Amana PTH123B25AJ Heat Pump Air...
Jan 16, 2011 | Cfm Daikin R410a Split System Air...
May 17, 2010 | Dometic Rooftop RV Air Conditioner
Aug 01, 2009 | Samsung AW0603B Air Conditioner
Jul 05, 2009 | General Electric Heating & Cooling
Jun 25, 2009 | LG Heating & Cooling
Jun 06, 2009 | Dometic Rooftop RV Air Conditioner
Jun 27, 2008 | Danby DPAC8020 Air Conditioner
174 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: