Question about Goodman GMS90703BXA Heater
I am a service tech and trying to help out a friend. He said his a/c is not working. Found the unit is completely out of freon. The leak was on one of the distributor tubes that go from the back side of the metering device to the indoor coil. I replaced the indoor coil and weighed in the charge. My head pressure is now running 150psi and suction pressure is going into a vacumm. In the heat mode the high side goes to 250 psi and suction is around 45psi. I am thinking I have a blockage but cannot figure out where. I checked to insure the new metering device that came with the new coil was the same size. can you give me some more ideas on what to check next.
A thermo-laser reader will let you know if, and where you may have a resrtiction by giving abnormal, or various temp. readings. Make sure that your filter line drier is good as well. If the drier has not been replaced, i would suggest that first.
Posted on Aug 16, 2008
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jul 27, 2017 | Goodman Heating & Cooling
Apr 20, 2014 | Goodman CKL42AR42 Air Conditioner
Aug 02, 2013 | Goodman Heating & Cooling
Jul 18, 2012 | Goodman Heating & Cooling
May 25, 2011 | Amana Heating & Cooling
May 16, 2011 | Goodman CKL42AR42 Air Conditioner
Sep 08, 2010 | Goodman CKL42AR42 Air Conditioner
Jul 28, 2010 | Goodman Heating & Cooling
Jun 16, 2009 | Goodman CLJ36AR42 Air Conditioner
Jun 13, 2009 | Goodman CKL42AR42 Air Conditioner
45 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: