Question about Goodman GMS90703BXA Heater
I am a service tech and trying to help out a friend. He said his a/c is not working. Found the unit is completely out of freon. The leak was on one of the distributor tubes that go from the back side of the metering device to the indoor coil. I replaced the indoor coil and weighed in the charge. My head pressure is now running 150psi and suction pressure is going into a vacumm. In the heat mode the high side goes to 250 psi and suction is around 45psi. I am thinking I have a blockage but cannot figure out where. I checked to insure the new metering device that came with the new coil was the same size. can you give me some more ideas on what to check next.
A thermo-laser reader will let you know if, and where you may have a resrtiction by giving abnormal, or various temp. readings. Make sure that your filter line drier is good as well. If the drier has not been replaced, i would suggest that first.
Posted on Aug 16, 2008
Tips for a great answer:
Dec 29, 2010 | Goodman Heaters
Oct 05, 2010 | Goodman Heaters
Aug 28, 2010 | Goodman Heaters
Jun 22, 2010 | Goodman GMS90703BXA Heater
Dec 17, 2009 | Heaters
Oct 26, 2009 | Heaters
Oct 16, 2009 | Goodman GMS90703BXA Heater
Jun 09, 2009 | Goodman GMS90703BXA Heater
Nov 03, 2008 | Goodman GMS90703BXA Heater
43 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: