Question about LG Heating & Cooling
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
SOURCE: i have i lg cassette
Ch-2 Indoor Pipe Sensor or Outdoor Sensor Assy fault, Open or Short. Disconnect from PCB and measure resistance. Air sensor = 10 kOhm at 25C, Pipe sensor = 5
kOhm at 25C. If not replace sensor.
Posted on Jan 04, 2011
Hello, that code indicates a low refrigerant charge. The problem with window units is that if they develop a leak it usually gets pretty costly to repair them, in some cases it is better to buy a new unit if the repair will cost more than a new unit.
Posted on Oct 03, 2011
Tips for a great answer:
Mar 03, 2018 | Carrier Heating & Cooling
Oct 21, 2013 | Heating & Cooling
Oct 09, 2011 | Washing Machines
Aug 22, 2011 | LG WD-1280FHD Front Load Washer
Jun 28, 2011 | LG WD-1080FD Front Load Washer
Jun 16, 2011 | LG Washing Machines
Mar 06, 2011 | LG DLE2514 Electric Dryer
Jan 04, 2011 | Heating & Cooling
80 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: