Question about Amana Heating & Cooling
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Capacitor, dirty condencer coil causing the motor amps to run too high. But most likely worn bearing on blade side of motor causing it to pull to one side causing it to over heat and shut down. Sleve bearings should have no side play.
Posted on Jun 28, 2009
be aware that not repairing this asap that you are causing yourself more problems First I would change out the fan capacitor and see if this could be the problem. Secondly if the capacitor isn,t the problem change out the motor . By continuing to allow the system to cycle like this the compressor will take a dive on you costing more . Good Luck
Posted on Aug 04, 2009
Testimonial: "Yes, it's dual run capacitor problem. I used a stick to spin the fan blades and it starts to slowly spin and up to normal speed, so motor is good."
Tips for a great answer:
Aug 06, 2014 | Amana Refrigerators
Apr 09, 2013 | Amana Refrigerators
Nov 30, 2012 | Amana ABB1921DE Bottom Freezer...
Jul 29, 2011 | Amana Quiet Zone 12M12TA Air Conditioner
Jun 21, 2010 | Amana ACD2232HR Side by Side Refrigerator
Aug 11, 2009 | Amana PTH123B25AJ Heat Pump Air...
Aug 04, 2009 | Amana PTH123B25AJ Heat Pump Air...
Jun 11, 2008 | Amana PTH123B25AJ Heat Pump Air...
99 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: