Question about LG Heat cool Window Air Conditioner
Hello, the evap coil will freeze from either low airflow or low charge. I would clean the coils, check air filter and replace or clean if dirty. If you have a thermometer measure the air entering the ac and the air leaving the ac, the differance should be 15-20 degrees, measure this after cleaning the coils. If it still is below 15 degrees the unit is underchraged.
Posted on May 26, 2011
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jul 03, 2011 | Carrier Heating & Cooling
Jan 31, 2011 | Electrolux Heating & Cooling
Jun 12, 2010 | Hitachi RAS-09UH Air Conditioner
Jun 19, 2010 | Friedrich QuietMaster® KS12L10...
May 28, 2010 | Honeywell Electronic Programmable...
Jun 04, 2008 | Weather King 10AJA2501AH Air Conditioner
May 20, 2008 | Goodman CKL60AR60 Air Conditioner
76 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: