Question about Sharp Heating & Cooling
It is probably either the high pressure switch or the frost control. The high temp switch usually trips because the condenser coil is dirty which does not allow it to exhaust heat very well. The frost control will trip if the system gets below 39 degrees on the pipes. This is usually do to low refrigerant or dirty filters. Good Luck!
Posted on Jul 03, 2008
SOURCE: air conditioner
I managed to find the people who supplied the unit, it was still under warranty, and they said it was the thermistors (temprature probes, they replaced both of them) It is now working perfectly!
Posted on Sep 24, 2008
are you speaking of the outside fan or inside? compressor should be a little warm but not boiling hot. the unit could be low on freon. if low it will run a while but the compressor will overheat and shut off leaving the fan running by itself ouside. if nothing outside is running check power. if you have power check the contacted outside to make sure it's pulled in. contacters are bad about going out on goodman untis. Also ants can get under contacts.
Posted on Jun 18, 2009
SOURCE: Will not cool properly.
You have either a faulty thermostat, dirty condenser and evaporator or a faulty run capacitor. Need to service soon before the compressor is damaged. Sea Breeze
Posted on Jul 06, 2009
Tips for a great answer:
Jan 10, 2017 | Heating & Cooling
Jan 08, 2017 | Amcor Heating & Cooling
Jan 07, 2017 | Heating & Cooling
Jan 06, 2017 | Heating & Cooling
Jan 05, 2017 | Mitsubishi Heating & Cooling
Jan 02, 2017 | Heating & Cooling
Dec 31, 2016 | Heating & Cooling
Jan 03, 2015 | Heating & Cooling
Nov 11, 2014 | Heating & Cooling
Jun 29, 2014 | Heating & Cooling
45 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: