Question about Heating & Cooling
What you need to do is disconnect the compressor at the electrical access on the side of the unit. Check each wire to the grounding screw using ohm meter if you get continuity your compressor is shorted do the same thing for you condenser fan. I bet your compressor is shorted. Make sure power is off and remember where the wires go. Trace the wires that go to compressor back to the contactor and capacitor and disconnect them there. If this help please rate me and do a testimonial.
Posted on May 25, 2011
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Nov 13, 2014 | Goodman Manufacturing Goodman ARUF48D14...
May 16, 2014 | Goodman CLQ36AR49 Air Conditioner
May 03, 2014 | Goodman Manufacturing Goodman GSZ130301...
Mar 25, 2014 | Goodman Heating & Cooling
Jan 06, 2014 | Electrical Supplies
May 20, 2010 | Goodman CLQ36AR49 Air Conditioner
Aug 22, 2009 | Goodman Heating & Cooling
Jun 04, 2009 | Goodman CLQ36AR49 Air Conditioner
Dec 20, 2008 | Goodman CLQ36AR49 Air Conditioner
Oct 22, 2008 | Haier Energy Star ESA3183 Air Conditioner
183 people viewed this question
Usually answered in minutes!