Question about Heating & Cooling
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
There could be a few possibilities, but I will tell you the most prevalent ones.....Dirty air filter or dirty indoor coil, bad blower, restricted air etc. The other is too low on freon. Turn ac to off and fan switch to on...wait 45 minutes and try again by setting thermostat no lower than 72. While waiting the 45 minutes check the filter , blower, and indoor coil.
Posted on May 15, 2010
Just run it in fan only mode for a while to dry it out...
You will not hurt anything...
Here is a tip about troubleshooting your air conditioner...
There are many things that can cause your air conditioner not to cool…
Air Conditioner Trouble -Review the Possibilities
Posted on Aug 21, 2010
Remove the thermostat face and place a jumper between R and Y. The outside unit should come on. If it doesn't, check for 24vac between R and C or R and Y. If you don't have it then you need to check the transformer. Check for 24vac on the transformer secondary and 120vac on the transformer primary. If you don't have power on the primary, check for a blown fuse or tripped breaker. If you do have power on the primary but nothing on the secondary, you need a new transformer. If the unit does come then the thermostat is the problem.
If the transformer is good and the unit doesn't start when you install the jumper then you have a problem in the outside unit. It could be the contactor coil which you can check with an ohmmeter. It could also be a low or high pressure switch or and overload all of which you can also check with an ohmmeter. Let me know what you find.
Posted on Nov 08, 2010
Tips for a great answer:
Sep 18, 2015 | Heating & Cooling
Aug 28, 2014 | Heating & Cooling
Jun 20, 2011 | Franklin Industries Franklin Chef Ice Cube...
Apr 16, 2011 | Heating & Cooling
Mar 27, 2011 | Heating & Cooling
Oct 07, 2009 | Konexx Phone 2 PC Basic (PHONE2PC)...
Jun 23, 2009 | Freezers
Apr 11, 2009 | Coleman Mach 15 Air Conditioner
53 people viewed this question
Usually answered in minutes!