Question about Teledyne Laars Laars Lx Pool Heater / 400,000 Btu / Propane Gas
Check to see if 24 volts ac to the gas valve if not bad gas valve or no gas supply to it
Posted on Mar 19, 2016
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
You have no flame rectification.....LLD series heaters check for a signal through the flame to ground; if the module does not detect this signal, it go through two more trials for ignition and then lock out the module. There should be a flame rod and it may need cleaning. I use steel wool.
Posted on Jun 28, 2009
Tips for a great answer:
May 08, 2015 | Teledyne Laars Laars Lite 2 Pool Heater...
Sep 13, 2013 | Jandy Laars Lite2 Lj 250,000 Btu Heater
Jan 27, 2012 | Teledyne Laars Pool & Spa
Dec 10, 2011 | Teledyne Laars Laars Lite 2 Pool Heater...
May 06, 2011 | Teledyne Laars Laars Lite 2 Pool Heater...
Jan 26, 2011 | Teledyne Laars Pool & Spa
Oct 09, 2009 | Teledyne Laars Pool & Spa
May 05, 2009 | Teledyne Laars Laars Lite 2 Pool Heater...
148 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: