Question about Heating & Cooling
Turn everything off your coil is frozen over and destroying the furnace. The furnace has water on the flame sensor and it thinks the gas is on but it isnt. The water is grounding out the flame sensor. If there is no water damage to the circuit board all you have to do is dry your flame sensor off and you should be fine. Now for the frozen coil you have a freon leak most likely or an air flow issue but you have to thaw the coil out completely before you can find out the problem. Check your air filter is it clean make sure your blower inside the furnace is rotating. If all these things check out ok you have to get the A/C charged with freon you have a leak. If this help please rate me and do a testimonial.
Posted on May 23, 2011
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Nov 01, 2017 | Coleman Heating & Cooling
Mar 02, 2017 | Coleman Heating & Cooling
Dec 30, 2015 | Coleman Heating & Cooling
Feb 14, 2014 | Coleman 7990-319p Evcon Gas Furnace...
Sep 21, 2011 | Coleman Heating & Cooling
Feb 10, 2011 | Coleman Propane Forced Air Heater...
Jan 23, 2011 | Coleman Propane Forced Air Heater...
Nov 20, 2010 | Coleman Heating & Cooling
Mar 31, 2009 | Coleman Propane Forced Air Heater...
Oct 25, 2008 | Heating & Cooling
120 people viewed this question
Usually answered in minutes!