Question about Heating & Cooling
Either defective sensors, or check the flow temperature going into the plate heat exchanger, if this getting very hot, but not circulating out the other side, it will probably be a blocked or restricted - replace
Posted on Mar 03, 2009
Maybe the diverter valve motor is not working B&Q ~£12.
Posted on Dec 11, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 17, 2011 | Heating & Cooling
Nov 03, 2010 | Heating & Cooling
Nov 06, 2009 | Ruud Matching Split Air Conditioner
Dec 31, 2008 | Heating & Cooling
Nov 01, 2008 | Heating & Cooling
Oct 05, 2008 | Heating & Cooling
Aug 05, 2008 | Heating & Cooling
223 people viewed this question
Usually answered in minutes!