Question about Heating & Cooling
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: Not a cadet but a King
shut off the breaker, then, remove the front grill. look for a device about the size of a nickel. could be fastened to the upper case. this is called a klixon overload. there are numbers stamped into the side of it. one of these are either temperature or an amperage value. get a replacement from an electrical supply house. it is probably blown. it is in series with the element. its purpose is to open [then reset] when an increase in current is evident. it is a bi-metal device - two dissimilar metals that bend at different rates when current is applied to it and opens a set of contacts.
Posted on Nov 16, 2007
SOURCE: Cadet wall heater
Since I don't know what model of heater you have there might be a reset button to reset or an over temp switch (button sensor with 2 wires going to it) that needs to be replaced. You might check the recall list to see if this one has been recalled and should not be used.
Posted on Oct 20, 2008
first try to pull out the little white button on bottom left side. if it is already pulled out, then take cover off, lightly press on the center dial as you adjust the little adjusters that are in the dial. should be two of them, the first should say off set to 90, second one says on set to 130or 135. these steps may work. if not then one of the wire connections may be loose.
Posted on Apr 26, 2009
I work in a motel and replace these heaters quite often, Cadet C202, a 240v 2000 watt wall heater. Most of the time when they blow cold air it's because the heating element is broken. First turn off the circuit breaker, then remove the heater from the wall. If you take out three screws, slide the top cover off, bend the two little tabs and take out the heating element, you can examine it and usually you will find a place where it is broken, it's like a big spring. Replacement elements can be ordered from online stores such as reliableparts.com Be very careful, 240 VAC is very dangerous! <!-- from fixya rte -->
Posted on Aug 16, 2010
Tips for a great answer:
Mar 21, 2017 | Coleman Heating & Cooling
Oct 18, 2014 | Cadet Manufacturing Heating & Cooling
Jul 02, 2013 | Ruud UBHC Air Conditioner
Mar 24, 2010 | Cadet Manufacturing Com-Pak Plus C151...
Feb 22, 2010 | Heating & Cooling
Dec 31, 2009 | Cadet Manufacturing 67507 Heater
Jun 17, 2017 | Heating & Cooling
Nov 21, 2008 | Heat Controller Thru-Wall/Window Air...
65 people viewed this question
Usually answered in minutes!