Question about Heating & Cooling
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
If you know where the high limit switch is you can always cut the two wires and wire them together causing the limit to close. But what you have to watch out for is why the high limit is not closing. That means in your return air either you have a dirty return air duct, dirty filter, or you don't have all your registors open to allow the heat to escape the heat exchanger. Just watch over riding the system. The high limit switch should either be on or behind the blower, in the middle of the system right under the heat exchanger. any other questions about hvac just ask.
Posted on Jan 17, 2009
Tips for a great answer:
Aug 10, 2014 | Heating & Cooling
Oct 20, 2013 | Emerson Lennox Ducane Armstrong Furnace...
Oct 19, 2013 | Emerson Lennox Ducane Armstrong Furnace...
Mar 07, 2011 | Heating & Cooling
Mar 08, 2010 | Heating & Cooling
Jan 10, 2010 | Armstrong H 67 1PH Bf In Line Circulator...
192 people viewed this question
Usually answered in minutes!