Question about Heating & Cooling
You need to get low voltage wire known as 5 wire. run wires thru wall to stat and furnace Red wire goes to R terminal white to W terminal Green to G terminal Yellow to Y terminal on both the stat and furnace circuit board. Now you need a wire called 2 wire low voltage wire run that from furnace circuit board to outside A/C. At furnace hook red wire to Y terminal and white to C terminal doesnt matter which ones you hook up at outside unit. Do it just like i told you this will work properly.
If this helps please rate me.
Posted on May 20, 2011
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Jun 02, 2017 | Heating & Cooling
Nov 17, 2014 | Heating & Cooling
Sep 21, 2014 | Heating & Cooling
Feb 14, 2012 | Heating & Cooling
Aug 10, 2011 | Heating & Cooling
Nov 03, 2009 | Intertherm P3RC-030K Air Conditioner
Apr 11, 2009 | Heating & Cooling
Apr 04, 2009 | Heating & Cooling
252 people viewed this question
Usually answered in minutes!