Question about Heating & Cooling
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: i have a Fujitsu ASTA24LCC
Check your filters. Manual says they need to be cleaned every two weeks under normal operation (and in my case more often during renovations). It seems it may not take much to limit air flow enough for the indoor unit to trip out. Hope this helps.
Posted on Aug 24, 2008
CA: Compressor Discharge Sensor Fault
Contact a qualified service technician and have them replace this sensor.
Posted on May 04, 2010
signal of indoor
1、Check whether two sets of plugs on the outlet end of
the motor have loosed from the socket of the
electric control board, insert it firmly when loosing.
2、Check whether the indoor motor has damaged, the
motor should be replaced when it is damaged
3、 Check whether the controllable silicon and other
components on the electric control board have
damaged, replace the controllable silicon or electric
control board when they are damaged.
Posted on Jun 26, 2010
Tips for a great answer:
Apr 29, 2016 | Heating & Cooling
Aug 10, 2013 | Soleus Ductless Mini Split 18000 Air...
Dec 18, 2012 | Dometic 3313192.000 White Single Zone LCD...
May 01, 2012 | Heating & Cooling
Aug 23, 2011 | Heating & Cooling
Dec 12, 2010 | Stoves Heating & Cooling
Dec 10, 2010 | Heating & Cooling
Dec 10, 2010 | Mitsubishi MSZ-A15NA Split System Air...
Aug 25, 2010 | Heating & Cooling
161 people viewed this question
Usually answered in minutes!