Question about Heating & Cooling
Assuming this is a standard unit the thermostat connections you will use: Y, R, G, W and possibly C.
Run two conductor thermostat wire to the condenser. The condenser will have two wires to connect. Connect the two conductors to the condenser wires and run them in to the air handler.
At the air handler, connect the two condenser wires to: Y (yellow) and C
Run 4 or 5 conductor thermostat wire from the air handler to the thermostat. At the thermostat, connect the yellow wire to Y, the white wire to W, the green wire to g, and the red wire to r.
At the air handler, connect the thermostat wires: White to w1, yellow to Y, green to G, and red to R
*Y will now be connected to the thermostat and the condenser
*If you have 5 conductor wire to the thermostat, connect the last wire (which is probably blue) to C
At the air handler, connect the last wire (blue) to C. This will enable you to have 24 volts at the thermostat in case the thermostat actually requires 24 volts to operate it.
Posted on May 19, 2011
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Apr 02, 2011 | Goodman Heating & Cooling
Jul 20, 2010 | Heating & Cooling
Jul 17, 2010 | Ruud UBHC Air Conditioner
Apr 21, 2010 | Heating & Cooling
Nov 14, 2009 | Heating & Cooling
Oct 16, 2009 | Goodman GMS90703BXA Heater
Apr 28, 2009 | Heating & Cooling
Oct 09, 2008 | Goodman Heating & Cooling
Jun 12, 2008 | Quasar HQ2052UH Air Conditioner
2,634 people viewed this question
Usually answered in minutes!