Question about Heating & Cooling
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: I just purchased a home
They have good listings on their web site.
That link should be to your model. When you click on the link for your manual (installation instructions)l, if it doesn't download. Right click on the link, and select download
So what is the problem?
Posted on Aug 12, 2010
Error Code ROL is "HEAT ROLL-OUT SAFETY SWITCH OPEN". The heater is equipped with a cutoff device to prevent flame roll-out in the event the heat exchanger becomes blocked. This is either a "manual reset", or "Single-use" type fusible link/thermal fuse, that must be replaced or reset after any over temperature conditions have been fixed. Excessive restriction in the heat exchanger flue passage may cause the switch to disable the heater. I don't know your exact model so I'm just generalizing. If you reset or replace the switch, and it trips/burns out again, then you need to address what is causing it. make sure the heater is cleaned out well and no debris is blocking the flue. I fthis doesn't help you can always try calling Raypak Service department at (805) 278-5300.
Posted on Sep 20, 2010
ROL code means Rollout.
This heater used a one time use switch in the cabinet on the left hand side.
The switch will look like a ceramic oval disk about 1.5" in diameter. It will have two wires coming from it.
This switch is one time use because it mean your heater is getting a bad burn. This could be happening due to:
1. High wind situation (could be random)
2. Incorrect gas supply
3. Incorrect venting (if indoor)
4. Obstruction on top of the burner tray.
There was a recall on the refractory kit with some of these models, causing the fire walls to crack off and fall on top of the burner tray. Thus causing the flames to rise too high inside the cabinet and therefor trip the rollout switch. The timeline for the recall matches your heaters date.
E-mail me if you need more help.
Posted on Dec 29, 2010
Tips for a great answer:
Jul 24, 2014 | Rheem Water Heaters
May 25, 2014 | Rheem 266K to 399K BTU Swimming Pool...
Apr 12, 2014 | Rheem Pool & Spa
Aug 18, 2013 | Rheem 266K to 399K BTU Swimming Pool...
Aug 12, 2010 | Rheem 266K to 399K BTU Swimming Pool...
Jul 04, 2010 | Solar Rheem Gas Fired Pool & Spa Heater...
May 08, 2010 | Rheem 266K to 399K BTU Swimming Pool...
Jul 05, 2009 | Solar Rheem Gas Fired Pool & Spa Heater...
58 people viewed this question
Usually answered in minutes!