Question about Procom ML060HPA Heater
I would trace gas line out and determine were you are getting gas and where it is not. With the gas on I would carefully loosen union or flex fitting going to gas valve.If you have gas there then retighten union and go to fitting on pilot line and check it.You should be able to get gas there by depressing pilot light button.If you have gas there then go to pilot assembly and remove it from gas valve and burner. Remove pilot orifice and carefully clean and blow thru pilot line to make sure it is not obstructed.
If you cannot get any gas thru gas valve then shut off gas before valve and remove inlet line. There should be a fine mesh steel screen there. Make sure it is clean.If you are getting gas to gas valve but not thru it then you probably need to replace gas valve. Thank you
Posted on May 17, 2011
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Dec 24, 2013 | Heating & Cooling
Dec 06, 2012 | Heating & Cooling
Jan 31, 2011 | Vanguard Heating & Cooling
Jan 01, 2011 | Williams 1556541 (LP) Gas Heater
Jan 04, 2010 | Bosch AquaStar 125FXKIT-LP 125FX Liquid...
Sep 10, 2009 | Heating & Cooling
Aug 08, 2009 | Stainless Garden Sun Steel Propane Patio...
Jan 02, 2009 | Procom ML300TBA Heater
Nov 21, 2008 | Rinnai Unvented Gas Zone Heater. 99% fuel...
Oct 04, 2008 | Reddy Heater RLP100 Portable Forced Air...
228 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: