Question about Coleman Mach 15 Air Conditioner
Fan problem could either be the starting capacitor or the motor itself. Often it would just be the capacitor and you could verify this by a humming/vibrating sound coming from the motor as if trying to turn but is not capable of. If it were the motor burned, the unit would have excessive current tripping the breaker or a fuse blowing.
Hope this be of initial help/idea. Pls post back how things turned up or should you need additional information.
Good luck and kind regards. Thank you for using FixYa.
Posted on Aug 13, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Aug 27, 2013 | Goldstar R1003 Air Conditioner
Sep 12, 2011 | Coleman Mach III Air Conditioner
Aug 19, 2010 | Heating & Cooling
Jun 26, 2010 | LG LWHD1500ER Wall/Window Air Conditioner
Jul 04, 2009 | Fedders A6X05F2D Air Conditioner
Jun 15, 2009 | Ruud UBHC Air Conditioner
Aug 25, 2008 | Carrier XHB123D X/Y Series Heat/Cool Air...
Sep 23, 2007 | Heating & Cooling
Jul 15, 2013 | Coleman Mach 15 Air Conditioner
131 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: