Question about Carrier Heating & Cooling
The compressor and Evap motor wil not shut off unless breaker is switched off. Is there a relay that controls this?
My carrier outside package unit the evaporator fan will not shut down
Posted on Jun 15, 2013
Sounds like your contactor is stuck closed.This is the part that high voltage connects to and lets power through to the compressor and condenser fan motor when you get a call for cooling.If you go to pull it out,kill the power outside AND at the furnace.
Posted on Aug 12, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 23, 2013 | Dometic Rooftop RV Air Conditioner
Jun 22, 2012 | Carrier Heating & Cooling
Sep 08, 2010 | Carrier 38CKC060 Air Conditioner
Aug 09, 2010 | Carrier Heating & Cooling
Apr 04, 2010 | Carrier 38CKC048 Air Conditioner
Aug 19, 2009 | Carrier Heating & Cooling
Jun 05, 2009 | Carrier 38CKC036 Air Conditioner
Mar 30, 2009 | Intertherm P3RA-036K Air Conditioner
Jul 25, 2008 | Dometic Rooftop RV Air Conditioner
May 29, 2008 | Carrier 38BRC048 Air Conditioner
119 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: