Question about Dayton Heating & Cooling
Line is L1 L2 L3 to line voltage. wire nut 4-7 together wirenut 5-7 together and wirenut 6-9 together connect 123 to line for low voltage 123 together 456 together 679 together. This works on all dual voltage 3 phase motors. Some of the newer Daytom motors have a plug that you just turn for changing voltage. Rudty
Posted on Jun 07, 2009
SOURCE: Need wiring Diagram for a
Dayton is a product of Grainger Industrial supply. You can contact Product Information and Parts Help at 800-323-0620 or their Tech Service Dept at 888-361-8649. I'm sure they can help you. Just have the Model Number and Serial Number available.
Posted on Mar 08, 2011
SOURCE: i got a dayton 2hp.
That motor is a three phase motor and will not run on 110 volts. It is also a high RPM motor with a lot of torque and MUST be mounted to a solid surface before it is powered up or it could rip your arm off as it flies across the room. If you have access to three phase power then you could power that motor but not with standard household electrical service.
Heres a link to some info for it
Posted on Jun 17, 2011
Tips for a great answer:
Jan 23, 2016 | Dayton Dryers
Mar 23, 2014 | Dryers
May 21, 2013 | Pool & Spa
Oct 12, 2012 | Dryers
Sep 28, 2012 | Dayton Permanent Split Capacitor Motor Fan
Feb 08, 2011 | Dayton Permanent Split Capacitor Motor Fan
Jan 14, 2011 | Dayton Permanent Split Capacitor Motor Fan
Jun 05, 2010 | Dayton Audio Dayton 6K138 CapacitorStart
Dec 13, 2008 | Dayton Permanent Split Capacitor Motor Fan
88 people viewed this question
Usually answered in minutes!