Question about Honeywell Programmable Thermostat Heater
If you have a forced air furnace with an air conditioner attached make sure you have a jumper wire between Rh and Rc. If the Bryant thermostat had a wire hooked up to C you do not want to hook this up to Rc. Just cap it off and put it back in the wall or disconnect that wire down in the furnace.
Posted on Jul 21, 2009
Some programmable thermostats require a comon wire to the transformer side of the 24V transformer. Check and see if this is true. And then look and see if your old thermostat had a "c"terminal used. Also would help if I knew the terminal designations your original thermostat had and the new one has.
If this helped you please rate me accordingly as high as you can and if you need more information please post back.
Posted on Apr 28, 2009
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Mar 01, 2017 | Honeywell Heating & Cooling
Nov 01, 2015 | Honeywell Ct87n1001 The Round-heat/cool...
Nov 17, 2014 | Honeywell T6360b1028 Room Thermostat
Nov 07, 2014 | Honeywell CT87N - Round Heat/Cool...
Jan 10, 2014 | Heating & Cooling
Aug 13, 2017 | Heating & Cooling
Apr 21, 2010 | Honeywell Heating & Cooling
Apr 21, 2010 | Honeywell Heat/Cool Thermostat
Jan 05, 2009 | Honeywell Programmable Thermostat Heater
Jan 18, 2008 | Honeywell CT87B ROUND HEATING&COOLING...
Jun 29, 2016 | Honeywell Programmable Thermostat Heater
Apr 27, 2016 | Honeywell Programmable Thermostat Heater
253 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: