Question about Amana Heating & Cooling
Are the wires going to capacitor correct. You have two sides to the capacitor one side is compressor or herm as stated on top the fan. should have one wire only on fan side then two wires to the common side and one wire to herm side. trace out the wires I'm sure it's electrical and make sure you can see that it does in fact have a dual capacitor. Turn off all electrical supply before even touching this as you are around some big voltage. I do this everyday and I won't even get close unless I pull the safety disconnect on the side of the house. Get back to me and can help further. Ken
Posted on Aug 22, 2009
On top of the capacitor you will find the terminals marked. One will say C, or Com. The others will be marked fan and herm. There will be a hot wire going to C. Usually this comes of the top of the contactor and is red. Find the wire that runs to the compressor. It will likely be yellow. This will hook to the Herm. Next find the fan wire (probably brown) it will hook to the fan. Hope this helps.
Posted on Jul 14, 2010
Tips for a great answer:
May 23, 2015 | Amana Heating & Cooling
Nov 08, 2011 | Intertherm P3RA-048K Air Conditioner
Jun 24, 2011 | Amana Heating & Cooling
Jun 04, 2011 | Amana Heating & Cooling
Jan 18, 2011 | Amana Heating & Cooling
Aug 07, 2009 | Heating & Cooling
Jun 26, 2009 | Dometic Rooftop RV Air Conditioner
May 09, 2009 | Amana Comfort Zone 12M32PBEH Air...
Jan 17, 2017 | Amana Heating & Cooling
76 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: