My heat pump, in the air conditioning mode, has the internal fan running, but the outside unit does not come on, When checking the circuit board in the outside unit, it shows LED 2 flashing and LED 1 off. What is this LED indication, and does this indicate the problem with the outside unit? Model No. UPNE - 048JAZ
- If you need clarification, ask it in the comment box above.
- Better answers use proper spelling and grammar.
- Provide details, support with references or personal experience.
Tell us some more! Your answer needs to include more details to help people.You can't post answers that contain an email address.Please enter a valid email address.The email address entered is already associated to an account.Login to postPlease use English characters only.
Tip: The max point reward for answering a question is 15.
Are you using your Air conditioner as a Heat Pump (Making heat in the house)- or as an Air Conditioner (making COLD air in the house.)
If as a heat pump, then remember-- that the WARM coil is now inside the house-- and the COLD one is outside-- So, if it is COLD outside, there is not enough HEAT out there, to keep the coil from going below freezing-- The unit may have to be turned off, and allowed to defrost, if you want more heat from the Heat Pump-
Your unit is running in heat pump mode...hope you knew that you had a heat pump...
Anyway the problem would either be the thermostat or the reversing valve...
It will take some detective work to figure out exactly which is causing your problems...
Definately get this checked out. Some thing has shorted just enough to let voltage "Feed back" and keep the fan running. Could be capacitor, wires rubbed through each other, etc. A reset is a safety that is used when there is an overcurrent or over pressure situation. No reset set for this situation.
There is always an outside chance that if you touch the unit while standing on wet ground, you may get shocked. I firmly believe that something is allowing power to the fan in a feedback condition so don't let this go as it may cause damage to other parts.
Good Luck and let me know how you make out on this.
Check t-stat and make sure fan is set to "Auto", that might be why fan is running all the time, or it could be a fan relay that is stuck closed. It sounds like you A/C is over charged or you have a bad high pressure switch, this was a common problem with this manufacture especially in the heat mode.
Does the air handler take a minute or two to start, this would be normal so that it doesn't blow cool air into the house before the unit is warmed up. If not could be the fan relay is weak and needs replacing. As far as the outside unit it sounds like you need to check the refrigerant. In cooling they are 70/150 psi. This should be checked in cooling mode, once you turn it to heating mode the pressures switch bring heat inside the house instead of out. I hope this helps.
Check your wiring between the contactor and compressor for a short to ground, or check the compressor windings for short to ground.
With the Tstat off, the contactor should be open so the only way for the compressor to be trying to do anything is if the 110 volts from the unbroken side are traveling through the compressor to ground. Since 110v is not enough to run it, the overload is kicking it out, cooling off, and repeating the cycle. When you kick on the Tstat, the contactor is supplying voltage directly to ground without going through the resistence of the compressor windings and kicking the breaker.
Post back and let me know what you find.