Question about LG BG8000ER Air Conditioner
What is the Procedure of Heat Load Calculation
Plz define the Right Formula
Here are a few ways to calculate your BTU's.
Get ready to use that algebra you thought you'd never use.
1 Ton = 12000 BTU's
400cubic feet per minute (CFM) = 1 Ton on standard ac units (300 is an absolute minnimum)
BTU's air heat = difference in temp. ( ∆T ) x 1.08 x CFM
∆T = BTU's / (1.08 x CFM)
i.e. 65◦F entering your unit and 93◦F air leaving on a 12000BTU unit.
∆T = 28
CFM = 400
28 x 1.08 x 400 = 12096BTU's
Electric heat calculations.
BTU's = KW (killowatts) x 3413
Watts = Volts x Amps (single Phase) Most Homes))
Watts = Volts x Amps x Phase (this is for three phase units.)three wires and a ground))
120 volts 30 amps single phase (common)
120 x 30.0 x 1 = 3600 or 3.6KW 3.6 x 3413 = 12286BTU's
Posted on Nov 14, 2008
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Feb 15, 2015 | Garden
Feb 02, 2015 | Miscellaneous
Oct 27, 2013 | Office Equipment & Supplies
Aug 07, 2012 | Coleman Heating & Cooling
Jul 18, 2011 | Heating & Cooling
Mar 21, 2011 | Texas Instruments BA-II Plus Calculator
Jan 25, 2011 | Amana PTH123B25AJ Heat Pump Air...
Jan 21, 2010 | LG BG8000ER Air Conditioner
Dec 23, 2009 | Texas Instruments TI-30X-IISTK Scientific...
Jun 20, 2009 | Carrier Heating & Cooling
Jun 21, 2017 | LG BG8000ER Air Conditioner
2,973 people viewed this question
Usually answered in minutes!