Question about Heating & Cooling
Check the Liquid line drier. Make sure the temperature on either side of the drier is the SAME.
If there is no drier, and there is an expansion valve installed in the air handler, then it might be "hunting" or have some trash or non-condensibles in the lines. The Liquid line must be in the low to mid 200psi range. Is the condensor coil clean? It must be.
Also is the filter new and not too restirctive? Don't use one of those 3 month filters. Think about this, if it is so good, and lasts 3 months, then each month, it gets loaded more and more. Imagine the particulates collected over a 3 month period!
Hope this helps.
Posted on Aug 08, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jul 20, 2014 | Goodman Heating & Cooling
Aug 02, 2011 | Heating & Cooling
Jun 23, 2011 | Heating & Cooling
Sep 08, 2010 | Heating & Cooling
Jul 02, 2010 | Weather King 10AJA6001AH Air Conditioner
Jun 15, 2010 | Ruud UBHC Air Conditioner
Apr 17, 2010 | Weather King 10AJA6001AH Air Conditioner
Oct 07, 2008 | Goodman Heating & Cooling
Jul 29, 2008 | Heating & Cooling
Feb 23, 2017 | Heating & Cooling
180 people viewed this question
Usually answered in minutes!