Question about Air Conditioners
Check the Liquid line drier. Make sure the temperature on either side of the drier is the SAME.
If there is no drier, and there is an expansion valve installed in the air handler, then it might be "hunting" or have some trash or non-condensibles in the lines. The Liquid line must be in the low to mid 200psi range. Is the condensor coil clean? It must be.
Also is the filter new and not too restirctive? Don't use one of those 3 month filters. Think about this, if it is so good, and lasts 3 months, then each month, it gets loaded more and more. Imagine the particulates collected over a 3 month period!
Hope this helps.
Posted on Aug 08, 2008
Tips for a great answer:
Jul 20, 2014 | Goodman Air Conditioners
Aug 02, 2011 | Air Conditioners
Jun 23, 2011 | Air Conditioners
Sep 08, 2010 | Air Conditioners
Jul 02, 2010 | Weather King 10AJA6001AH Air Conditioner
Jun 15, 2010 | Ruud UBHC Air Conditioner
Apr 17, 2010 | Weather King 10AJA6001AH Air Conditioner
Oct 07, 2008 | Goodman Air Conditioners
Jul 29, 2008 | Air Conditioners
Dec 10, 2016 | Air Conditioners
180 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: