Question about Heating & Cooling
Here's the deal: If your Vitodens 100 has outdoor temperature sensing capability, either built in or via external aftermarket control such as Tekmar or other, and the temperature outside is above warm weather shut down (WWSD), then the boiler will not operate for space heating, but will operate to make Domestic Hot Water (DHW) only. Generally speaking WWSD is facoty set at 20*C, since this is normal room temperature so the boiler will not need to operate at temperatures above this number as it is warm enough outdoors to heat the house to comfortable levels.
If your Vitodens 100 does not have outdoor temperature sensing capability then you should check to see if your room thermostats are operational and calling for heat since the boiler is only responding to this on-off control based on room temperature. (turn up your room thermostats)
In both cases you need to make sure that your heating system's distribution pump and zone valves are operating correctly.
In any case you should be calling a heating contractor if you suspect that there is a problem with your boiler and/or heating system.
Posted on Aug 05, 2009
New diverter valve
Posted on Nov 25, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Aug 12, 2016 | Water Water Heaters
Feb 09, 2016 | Water Water Heaters
Jan 19, 2011 | Home
Sep 16, 2009 | Combi Centre DX - Mango
Mar 02, 2009 | Water Heaters
Feb 05, 2009 | Combi Centre DX - Mango
Oct 31, 2008 | Heating & Cooling
Aug 21, 2008 | Combi Centre DX - Mango
Apr 04, 2008 | Combi Centre DX - Mango
2,106 people viewed this question
Usually answered in minutes!