Question about Goldstar Heating & Cooling
Hi, if he is a a/c tech, he had to use silver solder to repair the leak. If he is using manifold gauges, he can charge it with out knowing the amount to put in by looking for how much it takes. The unit needs/HAS to be evacuated first! He can charge in the freon using the chart on his low side gauge, as he wants the evaporator temperature to be at 40degrees F, with the P.S.I. at 68 for R-22. Just start charging in, using gas not liquid slowly, watching the suction line, and stop when it starts to condensation the line. If the top of the compressor starts to condensate, it is over charged. I wish you the best.
A/C, & Heating Contractor
Posted on Apr 10, 2011
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jul 01, 2014 | Goodman CKL24AR24 Air Conditioner
May 16, 2010 | Heating & Cooling
Sep 08, 2009 | Heating & Cooling
Aug 24, 2009 | Goldstar R5208 Air Conditioner
Aug 20, 2009 | LG Goldstar GWHD5000 wall/window Air...
Jun 08, 2009 | LG Goldstar GWHD5000 wall/window Air...
May 24, 2009 | Goldstar LG LUCKY WG1800R Room Air...
Jul 17, 2007 | Goldstar R5050 Air Conditioner
54 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: