Question about Dayton Gas Furnace Heater
Sounds like the furnace control (low voltage) circuit is open, or in other words you either have a fuse blown or a limit switch that needs to be reset. Most newer furnaces have a small knife like fuse, usually 3 or 5 amp located directly on the circuit board. Limit switches that have a manual reset are usually located in the fire box just above the burner. There may even be a limit switch located on the blower assembly. If you fuse was blown, you may need to find out what caused the short in the circuit or it will do it again. If the limit switch was tripped, you need to turn the furnace back on and watch the flame to see if there is "roll out". It it continues to trip or blow fuses you need to have the unit serviced.
Posted on Apr 10, 2011
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
You should be seeing 120 volts to the igniter. Anything less requires either a replacement of the transformer, start relay or control module.
Posted on May 30, 2008
Is there a setting on the thermostat for Auto or Fan? If so, make sure it is in the Auto setting. You will have a contactor that turns on the elements and a relay for the fan. Follow the wiring diagram to see which relay energizes the fan then unplug it to see if the fan stops.
Posted on Nov 03, 2009
Tips for a great answer:
Sep 28, 2016 | 2002 Dodge Ram Pickup 1500
on Dec 30, 2009 | Heating & Cooling
Nov 12, 2012 | Heating & Cooling
May 31, 2010 | Heating & Cooling
May 13, 2010 | Heating & Cooling
Mar 12, 2010 | Heating & Cooling
Feb 19, 2010 | Heating & Cooling
Jan 27, 2010 | Electric York / Paragon A-111-20 Heat...
Jan 04, 2010 | Amana Comfort Zone 12M32PBEH Air...
Feb 08, 2009 | Carrier XHB123D X/Y Series Heat/Cool Air...
423 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: