Question about Heating & Cooling
SOURCE: air conditioner
Remote control units have diagnostic program in the
control, after 3 to 5 minutes of operating if the diagnostic
tools detect abnormal operation, then its shutdown the unit
to protect from damage. Thermistor sensor is one of the
parts that detect the operation of the unit. Out of range
or defective thermistor can shut the operation of the unit.
- If your indoor and outdoor is clean start the unit in cool mode and monitor the outdoor pipes. If your suction pipe is icing or dry then your unit is under charge, but if your suction is cold and sweating then the system is ok and sure that the thermistor sensor is defective.
- Out of range thermistor sensor in both return air and freeze up sensor can cause the tripping “off “ the unit. The resistance of both thermistor is 8 to 10k ohms, so can test by using ohm meter
Posted on Jan 12, 2008
This is a single speed permanent split capacitor motor for the condenser. One of the capacitor wires shows infinite resistance to hot and netral. The motor needs to be replaced.
Posted on Mar 31, 2009
Beaumark air conditioners are made by GE…head over to their site and download a manual for their air conditioners - they are very similar.
Posted on Jul 06, 2010
Mine has a model number of PCA061D.
If you remove the water capture reservoir, there is a sticker that has the model number.
Posted on Sep 29, 2010
Tips for a great answer:
Jan 10, 2017 | Heating & Cooling
Jan 08, 2017 | Amcor Heating & Cooling
Jan 06, 2017 | Heating & Cooling
Jan 05, 2017 | Mitsubishi Heating & Cooling
Jan 04, 2017 | Heating & Cooling
Jan 02, 2017 | Heating & Cooling
Jun 24, 2015 | Heating & Cooling
Jan 03, 2015 | Heating & Cooling
Nov 11, 2014 | Heating & Cooling
Jun 10, 2012 | Heating & Cooling
336 people viewed this question
Usually answered in minutes!