Question about General Filters 1042-LH Humidifier
Hello, first thing is check is the strainer going into the solenoid valve for sediment, if there is clean the strainer and reinstall. If the strainer in clean the check if you are getting 24 volts to the solenoid valve, if you have voltage and the solenoid does not let the water thru replace the solenod valve.
Posted on Apr 09, 2011
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 16, 2016 | GeneralAire Legacy 1040 Humidifier...
Mar 08, 2015 | Carrier Humidifiers
Feb 06, 2014 | General Filters 1099-LH Humidifier
Nov 24, 2011 | General Filters 1042-LH Humidifier
Mar 17, 2011 | General Filters 1042-LH Humidifier
Feb 21, 2011 | Humidifiers
Jan 25, 2011 | General Filters 1042-LH Humidifier
Dec 01, 2009 | General Filters 1042-LH Humidifier
Jan 16, 2009 | General Filters 1042-LH Humidifier
394 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: