My heat pump is frozen up today and it is 60 degrees outside and I have my heat set to 66 degrees. Is this normal?
You post is not clear as to where the freeze-up is occurring. I'm going to assume the outdoor unit is frozen up.
Heat Pumps don't generally freeze up at 60 degrees. If the ice around the unit has an uneven pattern (for example a thick spot around the center or at the very bottom) could indicate a low refrigerant charge. If the ice is even throughout, it may be one of the following:
*Sticking Contactor*.....turn the system off at your thermostat and check to make sure the unit outside shut off. If it doesn't turn off, it is likely to be the contactor.
*Failed Defrost Thermostat*.....if the defrost thermostat fails "open", the system will never go into defrost.
*Failed Defrost Control Board*......this could also prevent the system from going into defrost
*Failed Reversing Valve*........put your system in COOL mode and check to see if it will blow cold air inside approx 16 - 22 degF lower than room temperature.
*Failed/Failing Condensor Fan Motor*.......ensure the condenser fan motor is running during heat and cool modes. The condensor fan motor will not run in OFF/Satisfied Mode or in Defrost Mode.
I hope this helps. Good Luck! :-)
Mar 05, 2010 |