On a call for cooling the condenser starts and then the indoor fan comes on after a few seconds the indoor fan shuts off and then comes back on again and it keeps repating this. The control board red indicator light does blink 4 times when the fan goes off indicating there is a limit open. I only see a limit switch on the R leg coming from the transformer. I don't see anything else that would make the fan go on/off continuously. Any suggestions?
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need. goodluck!
- If you need clarification, ask it in the comment box above.
- Better answers use proper spelling and grammar.
- Provide details, support with references or personal experience.
Tell us some more! Your answer needs to include more details to help people.You can't post answers that contain an email address.Please enter a valid email address.The email address entered is already associated to an account.Login to postPlease use English characters only.
Tip: The max point reward for answering a question is 15.
Seems like it trying to start and then cuts out , possibly on overload. Try the machine on fan blow only , that will check the indoor unit to see if that is working. Then try cool or heat function while listening to the machine starting. If you hear a loud humming just as the fan starts, and then it cuts out, It could be a compressor issue. Possibly the start capacitor has failed.
Seems like the fan relay has stuck (Likely to be on the main indoor PC board) or if the machine was being used on heating mode, the indoor pipe sensor may have failed causing the fan to continue to run. Most air cons on heating mode, will keep the fan running for a few minutes after you switch off on heating mode to cool down the indoor unit before it turns off completely. The pipe sensor signals the main PC board to tell it that the unit has cooled down and can now turn off completely. If either of the above faults occur, the indoor fan will keep running all the time.
Either the condenser fan has bad bearings, or it has a defective fan capacitor.
Turn off the breaker to the outside unit.
Spin the fan blade by hand.
If the fan blade spins easily and will spin a few revolutions with no problem the fan bearings are good.
If not, replace the fan motor due to bad bearings.
I am pretty sure you fan motor is bad because with a bad capacitor the fan motor will not get up to speed and may just sit and overheat.
I'm leaning toward a bad fan motor.
! shut it down but leave the indoor fan on. check the filters and replace as needed. It also appears the drain is plugged or iced up. If ou can access the indoor coil you can service the drain and run some hot water thru the pan that catches the condensate. If you can see your indoor coil and you see a "lint blanket" on the indoor coil you will have to vacume it off as well. I hope this helps let me know Jon
Hi, I assume this is a split system, with the indoor and outdoor unit. If you are talking about the fan on the outdoor unit, this is the condenser fan motor. It is exposed to the heat of the ambient temp. and removing the heat from indoors. If you have a heat pump, this motor runs year around and gets a lot of use. I have seen the 5mfd run capacitor fail which could cause this motor not to start, but more than likely the condenser fan motor has burned out.If it is the outdoor unit you are talking about, can you hear the compressor come on when you start it? You may stand by the unit and have someone turn the t-stat to cool and see if you hear it come on. It will shut off after awhile due to high head pressure. But, if nothing happens, you may not be getting power from the breaker being tripped or a blown fuse at the disconnect box at the unit.Check these before calling out a tech.If you are talking about the indoor fan, make sure the panels are on good if its a gas unit as there is a door switch that is closed and if the panel is loose, it will stop the fan from coming on. The indoor blower motor may also be burned out. It shouldn't take more then an hour at the most to find out what is causing this problem. Could be a fan relay. I would recommend calling a qualified a/c Co. to come out and check this. Wish I was there and could be of more help. Good Luck, Sincerely, Shastalaker7
In order to accurately determine and diagnose the problem, a more detailed description of the problem needs to be communicated as opposed to normal operation of the system so a repair person can determine that there is in fact a problem. There's a big difference between solving a problem via text as opposed to seeing what is wrong in the field. They rarely are the same.
Goodman condenser sequence of operation on a matched system. Call for cool, condenser starts, 15-30 seconds later blower motor starts, cool satisfied, condenser shuts down, 15-45 seconds later blower motor shuts down. House heats ups and a call for cool via the thermostat starts another cycle.
Based on normal operation it is impossible to determine whats wrong with the information given. There are perhaps 5 voltage measurements in the system that you could be referring to.
first disconnect the green stat wire wire could be bad if still runs change the board on the indoor unit pull board and take to goodman store with model number and serial number its under warrenty they will give new one hope this helps also look at dip switches and instructions to make sure ok
is your indoor fan motor noisy? Right after it shuts off feel if it is extremely warm (carefull, may burn you if you leave your hand on too long). If it excessively hot, the motor is tripping on overloads located in the motor itself, probably the bearings are dragging. Check to see if it spins freely when spun by hand. If not replace motor. Make sure power is off while putting your hands in or around the fan