Question about Heating & Cooling
Is it a cracking noise or does it sound more like metal stress (expansion & contraction)? If it's metal expansion, there may be a loose duct connection or strapping. If it's not metal expansion and contraction, check the burners for cracks, due to humidity dripping on them. If that's the case, obviously, they will need to be replaced. But, the question then is, where is the over production of humidity coming from. Is the Condensator pump not working properly or is the drain clogged up?
These are the thinkgs you need to check first.
Hope this helped you troubleshoot the problem.
Posted on Apr 07, 2011
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Mar 25, 2018 | Goodman Heating & Cooling
Feb 13, 2018 | Goodman Manufacturing Goodman GMS80603AN...
Oct 25, 2013 | Goodman Manufacturing...
Feb 17, 2018 | Goodman Heating & Cooling
Oct 06, 2012 | Cozy Enclosed Front Console Heater 70,000...
Oct 06, 2012 | Goodman Manufacturing GMH950453BX - 45,000...
Oct 01, 2011 | Goodman GMS90703BXA Heater
Jan 23, 2011 | Goodman GMS90703BXA Heater
Oct 11, 2009 | Goodman GDS80904BNA Open Flame Heater
Feb 17, 2009 | Goodman GMS90703BXA Heater
68 people viewed this question
Usually answered in minutes!