Question about GE Tjk436f000 3pole 400a 600vac Circuit Breaker

# Breaker installed on generator. Keeps tripping under no load after approx. 1 minute of generator running

Posted by on

• Level 3:

An expert who has achieved level 3 by getting 1000 points

Superstar:

An expert that got 20 achievements.

All-Star:

An expert that got 10 achievements.

MVP:

An expert that got 5 achievements.

• GE Master

A tripping circuit breaker is an indication of an overload. You say there is no load on the breaker - how are you making this determination? Are you using an amprobe or some other meter?

A circuit breaker with NO load shouldn't ever trip. Likewise a circuit breaker carrying up to 80% of of the current it is rated for shouldn't trip either. Circuit breakers that carry more than 80% of their load will trip - if the load remains connected long enough. This is called "duty factor" or "service factor" The greater the load is in excess of 80%, the less time that the breaker will carry it before tripping.

An example of a 100 amp breaker with different loads on it (this 100 amp value was chosen for ease of doing the math):

80 amps - never trips
85 amps - trips after 48 hours
90 amps - trips after 16 hours
95 amps - trips after 8 hours
100 amps - trips after 4 hours
105 amps - trips after a few minutes
120 amps - trips after a few seconds
150 amps - trips instantly

This is only an example to show how a certain circuit breaker might trip under a load less than the rating stamped on the body or handle.

A circuit breaker that trips with no load or a load equal to or less than 80% of its rating is most likely defective. You need an amprobe or ammeter for amp readings. If the load is found to be 80% or less, there may be an issue of harmonics that is causing the tripping. You'll need to have special equipment and qualified persons to check harmonic problems. Most harmonic problems occur when the loads are not linear device (transformers). Examples of non-linear devices are "switching" (or solid state) power supplies like those in computers.

I hope this helps and good luck. Please rate my reply. Thank you.

Posted on Apr 07, 2011

Hi,
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
Good luck!

Posted on Jan 02, 2017

×

my-video-file.mp4

×

## Related Questions:

### I have a steamist lt90 that we recently installed. It stays on for about 5 minutes then trips the breaker. It was installed using #10 wire and a 30 am breaker. Any ideas?

!!!!!First look on data plate see what is the rated amperes and kW . Make sure what code is for steam generators.

Some steam generators do not recommend GFI circuits to avoid nuisance tripping.

If you can us GFI in circuit breaker you may need two hots a ground and a neutral.

As a rule
30 amps = #10 wire
40amps = #8 wire and
50amps = # 6.

Generators normally are 240vts the two hot wires connect to # 1 and #2 wires coming from unit.

Aug 26, 2015 | Dryers

### My generator start the breaker trips under load and stops engine but with out load no trips

First check the load and grounding, you will need to measure the amperage draw wih an ammerter, also check to see if it trips when a large unit like a motor or air conditioner starts, it may not be able to handle the inrush. Also be aware that if your breaker is a 30amp does not mean you can pull 30amp you can safely constantly draw 80% of that. Also check your grounding of the equipment you are powering.

Dec 09, 2013 | Yanmar Diesel 5500 Watt Pramac Generator

### Breaker keep triping on screen light shows P-06

Is it tripping under load? or not under load. If it is under load have breaker checked and unit tested on a load bank. If it trips under no load check for wiring shorts on the main AC lines to the plugs

Oct 02, 2013 | Kipor Electrical Supplies

### I have a 5kw generator it was working fine I use it on the oil fields to power my little rv suddenly every time I turn on the air con it trips the breaker and now im using a air compressor and at first...

A number of things can cause this. A sit worked before !
Basically:

Engines get older and can't hold HP which causes the rpm to slow and voltage dip, this causes a current increase and trips.

Breakers also get weaker especially if they trip a few times
HVAC and compressors pull approx 6 times the current to start as they do to run, once they have run a while, they build up higher head pressures which cause harder starting and more current draw, hence the breaker tripping.

It's hard to pin point which is the actual issue, but these all contribute.

Aug 08, 2013 | Briggs & Stratton Power Products 5,550...

### I have a troybilt 7000 gas generator that trips the main output breaker when under a load after 5 minutes

1. Make sure that the generator limit is not being exceeded.
2. Try checking and raising the rpm. If the engine can not sustain the load from the generator, it can/will trip the breaker.
3. If the carb is dirty or the engine runs poorly it can trip the breaker. Tune up the engine, clean the carb, make carb adjustments to correct substandard running conditions.

Jan 21, 2013 | Garden

### Generator circuit breaker keeps tripping

wet plugs,exceeding max load of circut,whatever it is running has a short in it.

Dec 21, 2012 | Buffalo Tools Pro-series 7000 Watt Silent...

### Heat / Cool unit runs approx 45 minutes then trips the breaker

Check the amperage of the breaker or change the breaker out completely with a new one. The tripping problem is that the breaker itself is heating up to the point that the bi-metal in the breaker (safety device) is throwing the breaker off. This could be the problem for you however, I would get an ampherage draw from the unit to insure that the breaker is the proper size for the unit. If you can find what kilowatt the unit is divide that number by the amount of current being supplied and that will give you the breaker size.

Good luck hope I helped you some

Dave

Jan 08, 2010 | Kenmore Heating & Cooling

### Genset starts and runs fine but the 30 Amp circuit breaker trips as soon as a load (AC) is applied. Started right up, ran half a day, but now when it starts the minutes I click on the ac the circuit...

What about when you have it powering the motorhome, without AC on, does it trip then? Do you have anyone you know with a multimeter and knows how to use it? How about buying a plug in voltage meter at a hardware store as a good start. You simply plug it in to a receptacle in your motorhome and it will tell you the incoming voltage and they are not very expensive. That will help diagnose generator problem.

Nov 01, 2009 | Watts Onan Portable Generator - 4000 ,...

### 40G quietpact rv generator shuts off the instant something is powered on. Sometimes it does run for about a minute before shutting down. Sometimes it's running and shuts down the instant the appliance is...

the fact that it's tripping the breaker on the genset would suggest the the problem is not at the generator but rather on the load side of the genny before anything else I would seperate the generator from the rvs electrical system and apply some other load some thing fairly heavy toaster heater ect.. the fact that it's stopping the generator is a little unusual but it could just mean that the electriacl panel has a relay that keeps the generator running when the power dies so does the generator .load test should point you in the right direction I,ve owned 4 motor homes and when I wish you luck I realy mean it.
Good Luck

Oct 09, 2009 | Guardian Rv Generator 4800 Watt, Gasoline,...

## Open Questions:

#### Related Topics:

2,080 people viewed this question

Level 3 Expert