Question about GE Zoneline AZ38H12DAD Split System Air Conditioner
My a/c is dripping water out the front... I pulled it out from the wall and it looks like the drain pan towards the outside is completely dry and all the water is pooling under the front of the unit and then dripping out onto the floor. Can anyone tell me if this sounds like it is the problem and if so, how do I fix it? I can see what looks like a little passage for the water in the styrofoam towards the left side and I guess it might be blocked? If so, how do I get to it to clean it out or do I have to call someone?
Is this a newly installed unit? The problem sounds like the sleeve is improperly installed. The sleeve should slope approximately 1/4 inch downward from inside to outside. This way the water will run to the back of the pan where it will be picked up by the slinger fan, or drain to the outside. Most likely this is the cause, not the styrofoam pan. If you need further info, you can contact me at greg.mcnary(at)airdistributors.com (replace (at) with @) and I can get you detailed installation instructions.
Air Distributors Company, Inc.
Distributors of GE Zoneline PTAC Units and
McQuay PTAC Units
Posted on Aug 06, 2008
Tips for a great answer:
Sep 12, 2011 | Kenmore 6000 Wall/Window Air Conditioner
Aug 26, 2011 | Kenmore Single Room Air Conditioner
Aug 04, 2011 | LG LS307HV Air Conditioner
Jun 27, 2011 | Air Conditioners
Jun 14, 2011 | Sanyo 09KHS51 Ductless Mini Split Air...
May 08, 2010 | Weather King 12AJA4201AH Air Conditioner
Oct 02, 2009 | Friedrich M18YE Air Conditioner
Aug 17, 2009 | Air Conditioners
Mar 24, 2009 | Air Conditioners
Sep 22, 2007 | Amana PTH123B25AJ Heat Pump Air...
Jan 15, 2014 | GE Zoneline AZ38H12DAD Split System Air...
1,712 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: