Question about GE Zoneline AZ38H12DAD Split System Air Conditioner
My a/c is dripping water out the front... I pulled it out from the wall and it looks like the drain pan towards the outside is completely dry and all the water is pooling under the front of the unit and then dripping out onto the floor. Can anyone tell me if this sounds like it is the problem and if so, how do I fix it? I can see what looks like a little passage for the water in the styrofoam towards the left side and I guess it might be blocked? If so, how do I get to it to clean it out or do I have to call someone?
Is this a newly installed unit? The problem sounds like the sleeve is improperly installed. The sleeve should slope approximately 1/4 inch downward from inside to outside. This way the water will run to the back of the pan where it will be picked up by the slinger fan, or drain to the outside. Most likely this is the cause, not the styrofoam pan. If you need further info, you can contact me at greg.mcnary(at)airdistributors.com (replace (at) with @) and I can get you detailed installation instructions.
Air Distributors Company, Inc.
Distributors of GE Zoneline PTAC Units and
McQuay PTAC Units
Posted on Aug 06, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Aug 04, 2011 | Breezaire WKS4000 (1000 cu. ft.) Wine...
Jul 21, 2011 | GE Heating & Cooling
Jun 14, 2011 | Sanyo 09KHS51 Ductless Mini Split Air...
Sep 01, 2010 | GE Zoneline AZ25E12D3B Air Conditioner
Jul 04, 2010 | GE ASL05LA Air Conditioner
Nov 14, 2009 | Heating & Cooling
Aug 18, 2009 | General Electric Zoneline® Deluxe Series...
Oct 29, 2008 | GE Zoneline AZ55H07D Air Conditioner
Oct 06, 2008 | GE Heating & Cooling
Sep 22, 2007 | Amana PTH123B25AJ Heat Pump Air...
Jan 15, 2014 | GE Zoneline AZ38H12DAD Split System Air...
1,727 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: