Question about Hayward 100kbtu Pool Or Spa Propane Gas Heater H100idp1
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
if ignitor sparks i'd say its okay, more likely a gas valve problem.are you sure gas supply is on and purged of air?make sure gas valve(the one gas supply threads into) is in the on position
Posted on Jun 21, 2009
You didn't say what terminals you jumped, but I assume it's the flow switch, or it could be the thermostat. The flow switch is located on the piping inside the heater. This flow switch is very important because if you didn't have water flowing through the heater it would oveheat. These do go bad or sometimes just get stuck depending on what type they are. If it's the thermostat, mounted on the front pane you're jumping, then either it or it's expansion bulb is faulty. GOOD LUCK Who needs a heater in JULY?
Posted on Jul 03, 2010
Testimonial: "Thank you, Yu have given me plenty to look into..."
Tips for a great answer:
Mar 05, 2015 | Pentair Mastertemp 250 Natural Gas Pool...
Mar 03, 2015 | Raypak Pool & Spa
May 05, 2013 | Heating & Cooling
Mar 01, 2017 | Dayton Heating & Cooling
Feb 27, 2017 | Heating & Cooling
Nov 07, 2011 | Electrolux EOG6330 Gas Single Oven
Jul 15, 2011 | Bosch 1600H-NG Natural Gas AquaStar...
Jul 01, 2010 | Hayward H Series Pool & Spa Heater 400k...
Feb 08, 2009 | Rheem 50 Gallon FVR NATGAS Water Heater...
Sep 01, 2012 | Hayward 100kbtu Pool Or Spa Propane Gas...
176 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: