Question about Heating & Cooling
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
There are a couple possibilities:
1. If this is the first time you've started them for the season, one of the compressors might be seized up from sitting over the winter. In which case, new compressor required.
2. If you've just had the compressor serviced including recharging the system, it's possible that the system is simply overcharged. This will stop the compressor from working and giving you the same symptoms as above. If this is the case, you should have the service people come back with some guages and recover some of the refrigerant and the compressor should be fine.
3. If the unit has been sitting and there is a slow leak then there is not enough pressure in the system to allow it to run. The compressor will shut down if there is not enough pressure, but since you say there is a smell, i really doubt this is the case.
Most likely it's #1 or #2 above. If you haven't had it serviced recently, then yeah, it sounds like you're in need of a new compressor.
Posted on Apr 16, 2008
Unit#2 -Sounds like the contacts on the master switch are welded closed or the switch is broken, Replacing the switch should fix this unit.
#1 is a little more difficult to diagnose. The compressor is being taken off line by a circuit that protects the compressor from damage either; 1- liquid refrigerant getting back to the compressor which can be caused by something as simple as a clogged return air filter or evaporator coil on a heat pump or 2- overload situation caused by a bad condenser motor or a clogged condenser coil. The first thing you need to do is clean both coils and replace the filter,. Then check to be sure your getting good airflow across both coils. I think it's most likely an airflow issue I hope this resolves the problem GL!
Posted on Jun 12, 2008
Sounds like your start capacitor may have gone bad. If you remove the shroud, there should be an access panel for the electronics. In there, you'll see one (or two) cylindrical parts with wires coming out the top. If one of them shows signs of something coming out of it, it's probably your start capacitor and it needs to be replaced.
You can view the installation/service manual for DuoTherms here at Bryant RV.com (it's a 3MB PDF file, so download with care). Look on page 28 for info on the capacitors.
Posted on Oct 13, 2008
I don't think these little units have a start capacitor but what I would do is check that the on/off switch wires to make sure they aren't loose. Also check the wires to the compressor for loose wires as well. It is possible that these are the first signs that the compressor is about to fail. They also can act up some when they haven't been used for awhile and then you try and start them up. Try running the unit for a few hours without asking it to cycle. It might just be a sticky valve.
Posted on Apr 13, 2009
Most of the time the capasitors are bad but it could be that the commpressor is bad or if it is a heatpump the low pressure switch could have it locked out or the contactor could be bad also
Posted on May 02, 2009
Tips for a great answer:
Jun 01, 2012 | GE Air Conditioner Main PCB - WJ26X10241
Apr 28, 2012 | GE Ahm18dp Air Conditioner Window Unit...
May 09, 2011 | Samsung Heating & Cooling
Aug 30, 2009 | GE APH10AA Air Conditioner
Jun 04, 2009 | Kenmore 76129 Air Conditioner
Feb 07, 2009 | Dometic Rooftop RV Air Conditioner
Jun 05, 2017 | Frigidaire Heating & Cooling
Jun 01, 2017 | Coleman Heating & Cooling
Apr 16, 2008 | Dometic Rooftop RV Air Conditioner
May 23, 2018 | Coleman Heating & Cooling
75 people viewed this question
Usually answered in minutes!