Question about Heating & Cooling
When the flames come on the control monitors the resistance inside a probe called a flame sensor. Of time carbon builds up on that sensor probe and the resistance does not read. When that happens the dang control shuts does and retrys to get confirmation of ignition. Get the sensor off there and clean it up with a dry brillo pad or sand cloth. Re install and check operation.
I have more HERE
If you need further help, reach me via phone at https://www.6ya.com/expert/dan_73bbd84fe1d95b61
Posted on Apr 06, 2011
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Nov 05, 2017 | Heating & Cooling
Mar 04, 2017 | Null Heating & Cooling
Dec 20, 2010 | Heating & Cooling
Nov 25, 2010 | Heating & Cooling
Mar 14, 2010 | Comfort Zone CZ-800 Heater
Dec 12, 2009 | Jackson 25 in. TempStar HH-ST...
Feb 06, 2009 | Carrier Heating & Cooling
Jan 17, 2009 | Honeywell Programmable Thermostat Heater
Oct 03, 2007 | Heating & Cooling
24 people viewed this question
Usually answered in minutes!