Question about Air Tools & Compressors
Some oil lubed compressors as well as oilless types have a bolt on rod journal that can be removed to allow motor to be seperated from pump. Others, however have journal either one piece to motor shaft or journal is pressed on. If you do not see bolt thru journal, most likely it will not seperate. Check with parts manual for more information as some motors have a removable iron core on the shaft (very difficult to remove and re-install). Good luck
Posted on Apr 08, 2011
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
May 27, 2015 | Air Tools & Compressors
Feb 07, 2015 | Garden
Feb 01, 2015 | Campbell Hausfeld Air Tools & Compressors
Feb 04, 2012 | Campbell Hausfeld Air Tools & Compressors
Dec 15, 2010 | Dewalt d55170 Electric powered air...
Jun 28, 2010 | Craftsman Air Tools & Compressors
Nov 09, 2009 | 2006 Chevrolet Trailblazer
Sep 26, 2009 | Coleman Air Tools & Compressors
Mar 24, 2009 | Coleman Air Tools & Compressors
Hello Tom , I'm sure i can help you with this.... I work on these units everyday. unfortuneately im not there to put my hands on it but i will explain as clearly as possible. The most common problem I tend to find with these units is that the control board and indoor fan motor tends to go bad in these quite often. If you put the unit in A/C MODE and/or Fan mode and set it to high if it will not speed up from low , then your problem could be in a couple different places. 1st. The bearings in the fan motor could be wearing down , 2nd The Control board could be bad in that its not telling the fan motor to speed up.
And when you tell me that the compressor doesnt run in that mode at any given time..... which the electric heat and heat pump itself works together so that when the load is really tough that the heat pump doesnt over work and in general saves life on your compressor.
Solution is this.
Take your indoor fan motor off and and drill out the rivits and it pulls apart easy, and replace the bearings and grease them.
ALIGNMENT OF THE FAN IS A MUST. doesnt cost much at all the fix this. Just a little time and bearings
Replace the Board in the control box
This my friend will definetly solve your problem. These problems i see everyday with these same units.
Oct 10, 2007 | GE Zoneline Deluxe Series Cooling &...
Oct 16, 2017 | Porter Cable Air Tools & Compressors
118 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: