Question about Carrier 38CKC024 Air Conditioner
Hello, sounds like the motor is opening on it's internal overload, This could be due to either a bad run capacitor or open motor winding. If you have a meter you can check the resistance of the motor by turning off power to the unit and placing one meter lead on the purple wire and the other meter lead to each other wire one at a time, you should have resistance if not the motor has a open winding and needs to be replaced. If the motor is fine then tne run capacitor is the problem and must be replaced.
Posted on Apr 03, 2011
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
New users get 2 Free calls (no credit card required) and instant help on almost anything you can think of (from cars to computers, appliances, handyman, and even pets).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jul 05, 2016 | Hunter Dryers
Sep 08, 2015 | Heating & Cooling
Aug 22, 2015 | Heating & Cooling
Jun 14, 2014 | Beverage-Air MT27 Beverage Cooler...
Jun 30, 2012 | Heating & Cooling
Sep 07, 2010 | Heating & Cooling
Jul 25, 2010 | Mercedes-Benz E320 Cars & Trucks
Jul 01, 2010 | LG Art Cool LA121CNP wall/window Air...
Aug 05, 2009 | Heating & Cooling
May 19, 2008 | Kenmore 72912 / 72914 / 72919 Bottom...
371 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: